This set of Power Systems Multiple Choice Questions & Answers (MCQs) focuses on “Electric Field and Potential of a Long Straight Conductor – 1”.

1. Shunt admittance of a transmission line comprises of ______

a) capacitance with conductance

b) capacitance with inductance

c) resistance with inductance

d) capacitance with susceptance

View Answer

Explanation: Shunt admittance is capacitance with conductance in the branch.

2. Conductance is the result of the leakage over the surface of insulators.

a) True

b) False

View Answer

Explanation: Conductance comes into the picture due to the leakage current over the conductor’s surface.

3. Charging current in the transmission line is _______________

a) drawn at open as well as closed end of the transmission line

b) drawn at closed end of the transmission line

c) drawn at open end of the transmission line

d) drawn at the shunt capacitance at closed end of transmission line.

View Answer

Explanation: Charging current in transmission line is drawn even when the far end of the TL is open.

4. A three phase 50 Hz transmission line has flat horizontal spacing with 3.5 m between adjacent conductors. The conductors are No. 2/0 hard drawn copper (outside diameter = 1.05cm). The voltage f the line is 110 kV. The capacitance to neutral per kilometre of line is

a) 0.00826 μF/km

b) 0.0826 μF/km

c) 0.01652 μF/km

d) 0.1652 μF/km

View Answer

5. A three phase 50 Hz transmission line has flat horizontal spacing with 3.5 m between adjacent conductors. The conductors are No. 2/0 hard drawn copper (outside diameter = 1.05cm). The voltage f the line is 110 kV. The capacitive reactance to neutral per kilometre of line is ____________

a) 0.384 x 106 Ω/km to neutral

b) 0.768 x 106 Ω/km to neutral

c) 0.284 x 106 Ω/km to neutral

d) 0.642 x 106 Ω/km to neutral

View Answer

6. A three phase 50 Hz transmission line has flat horizontal spacing with 3.5 m between adjacent conductors. The conductors are No. 2/0 hard drawn copper (outside diameter = 1.05cm). The voltage f the line is 110 kV. The line charging current per km of the line is _______________

a) 0.17 A/km

b) 0.34 A/km

c) 0.24 A/km

d) 0.48 A/km

View Answer

7. A three phase 50 Hz transmission line has flat horizontal spacing with 3.5 m between adjacent conductors. The conductors are No. 2/0 hard drawn copper (outside diameter = 1.05cm). The voltage f the line is 110 kV. The line charging current per conductor of the line is _____________

a) 0.085 A/km

b) 0.17 A/km

c) 0.12 A/km

d) 0.24 A/km

View Answer

Explanation:

C

_{n}= 0.00826 μF/km

X

_{n}= 1/ωC

_{n}

X

_{n}= 1/(100π* .284 *10

^{-6})

X

_{n}= 0.384 x 106 Ω/km to neutral

Charging current = Vn/Xn

Charging current = (110/√3)*1000/(0.384 *10

^{6})

Charging current = 0.17 A/km

Charging current per conductor = I/2

Charging current per conductor = 0.17/2

Charging current per conductor = 0.085 A/km.

8. A three phase 50 Hz transmission line has flat horizontal spacing with 3.5 m between adjacent conductors. The conductors are No. 2/0 hard drawn copper (outside diameter = 1.05cm). The voltage f the line is 110 kV. The reactive volt amperes generated by the line is

a) 31.4 kVAR

b) 62.8 kVAR

c) 42 kVAR

d) 56 kVAR

View Answer

Explanation:

C

_{n}= 0.00826 μF/km

X

_{n}= 1/ωC

_{n}

X

_{n}= 1/(100π* .284 *10

^{-6})

X

_{n}= 0.384 x 106 Ω/km to neutral

Reactive volt amperes generated by the line = (VL)

^{2}/X

_{c}

Reactive volt amperes generated by the line = 31.4 kVAR.

**Sanfoundry Global Education & Learning Series – Power Systems.**

To practice all areas of Power Systems, __here is complete set of 1000+ Multiple Choice Questions and Answers__.

**If you find a mistake in question / option / answer, kindly take a screenshot and email to [email protected]**

**Related Posts:**

- Apply for Electrical Engineering Internship
- Check Electrical Engineering Books
- Practice Electrical & Electronics Engineering MCQs
- Apply for Electrical & Electronics Engineering Internship
- Practice Electrical Engineering MCQs